Ex d IIB+H2 T6...T4 GbEx d [ia IIA or IIB or IIC Ga] IIB+H2 T6...T4 GbEx d I MbEx d [ia Ma] I MbEx tb III C T85°C...T135°C Db IP66Ex tb [ia Da] III C T85°C...T135°C Db IP66
This certificate is issued as verification that a sample(s), representative of production, was assessed and tested and found to comply with the IEC Standard list below and that the manufacturer's quality system, relating to the Ex products covered by this certificate, was assessed and found to comply with the IECEx Quality system requirements. This certificate is granted subject to the conditions as set out in IECEx Scheme Rules, IECEx 02 and Operational Documents as amended.
This Unit verification certificate is issued as verification that the Apparatus identified on page 1, was assessed and tested and found to comply with the IEC Standard list below. This certificate is granted subject to the conditions as set out in IECEx Scheme Rules, IECEx 02 and Operational Documents as amended.
The apparatus and any acceptable variations to it specified in the schedule of this certificate and the identified documents, was found to comply with the following standards:
As this is a Unit Verification Certificate, no QAR is applicable as this certificate is specific to the items listed by serial number or other unique identification.
The enclosures type EJB... use the flameproof enclosure certified as Ex Component covered by IECEx INE 14.0036U.
They can be fitted with operator covered by IECEx INE 14.0032U and a breathing or draining device covered by IECEx INE 12.0002U.
These enclosures are intended to contain mainly electrical and/or electronical "NIS" components, they can also contain "IS" elements covered by a separated IECEx certificate.
These enclosures get the degrees of protection IP66 in accordance with IEC 60529 standard.
- The gap of different joins is lower to those specified in tables of IEC 60079-1. - The width of the flameproof joints is superior to those specified in tables of IEC 60079-1. - For used in group I, during the installation, the user will take into consideration that the enclosures underwent only a shock corresponding to an energy of a low risk.