This certificate is issued as verification that a sample(s), representative of production, was assessed and tested and found to comply with the IEC Standard list below and that the manufacturer's quality system, relating to the Ex products covered by this certificate, was assessed and found to comply with the IECEx Quality system requirements. This certificate is granted subject to the conditions as set out in IECEx Scheme Rules, IECEx 02 and Operational Documents as amended.
This Unit verification certificate is issued as verification that the Apparatus identified on page 1, was assessed and tested and found to comply with the IEC Standard list below. This certificate is granted subject to the conditions as set out in IECEx Scheme Rules, IECEx 02 and Operational Documents as amended.
The electrical apparatus and any acceptable variations to it specified in the schedule of this certificate and the identified documents, was found to comply with the following standards:
As this is a Unit Verification Certificate, no QAR is applicable as this certificate is specific to the items listed by serial number or other unique identification.
The LED High Bay Area light (HBA) is a pendant floodlight rated at 100V to 277V, 50/60Hz, and up to 165W.The HBA comprises an aluminium lamp enclosure housing high power LEDs and their associated driver circuits. A glass lens is clamped in place by an aluminium frame, which is secured by 12 fasteners the heads of which are filled with epoxy resin to prevent removal.The HBA has an integral cable and an external suspension bracket.Variation 0.1Alternative version of the unit incorporating an increased safety terminal box.The terminal box electrically connected to the luminaire housing via a line bushing.The terminal box is assembled using silicone rubber ‘O’ rings. Up to two M20 or M25 apertures are provided in the sides of the terminal box.The unit so formed is designated as the HBA Series LED Luminaire with Junction Box, and is marked:Ex d e IIB+H2 T5 GbEx tb IIIC T100°C Db IP66Ta -40°C to +60°CVariation 0.2Alternative transportable version of the unit with a tubular stand to allow various mounting positions.The unit is fitted with an increased safety terminal box. An auxiliary external wire guard may also be fittedThe unit so formed is designated as the HBA Series Transportable Luminaire and is marked:Ex d e IIB+H2 T5 Gb Ex tb IIIC T100°C Db IP66Ta -40°C to +60°CVariation 0.3Alternative version of the unit incorporating the increased safety terminal box as above and fitted with an external transparent plastic lens guard. A warning label is fitted to indicate the cleaning method for the guard.The unit so formed is designated as the HBA Series LED Luminaire with Sand Blast Shield and is marked:Ex d e IIB+H2 T5 GbEx tb IIIC T100°C Db IP66Ta -40°C to +60°C
1. The HBA is a factory sealed product, do not attempt to open; return to the manufacturer for service or repair.2. The HBA is to be suspended such that no tension is applied to the supply cable.3. The integral cable is to be terminated in a suitable terminal or junction facility.4. The external plastic guard on the HBA Series LED Luminaire with Sand Blast Shield is to be cleaned with a damp cloth only.