Ex d IIC T4 Gb
This certificate is issued as verification that a sample(s), representative of production, was assessed and tested and found to comply with the IEC Standard list below and that the manufacturer's quality system, relating to the Ex products covered by this certificate, was assessed and found to comply with the IECEx Quality system requirements. This certificate is granted subject to the conditions as set out in IECEx Scheme Rules, IECEx 02 and Operational Documents as amended.
This Unit verification certificate is issued as verification that the Apparatus identified on page 1, was assessed and tested and found to comply with the IEC Standard list below. This certificate is granted subject to the conditions as set out in IECEx Scheme Rules, IECEx 02 and Operational Documents as amended.
The electrical apparatus and any acceptable variations to it specified in the schedule of this certificate and the identified documents, was found to comply with the following standards:
As this is a Unit Verification Certificate, no QAR is applicable as this certificate is specific to the items listed by serial number or other unique identification.
The motor earthing type EEx ME 12 C is used for earthing rotating elelctrical machines. It consists of an enclosure in type of protection flameproof enclosures. The electrical connection will be made by mounting.
Permitted range of ambient temperature
The security level of the flameproof joints is higher than in the standard IEC 60079-1 required security level. The exact gap dimensions are gettable from the manufacturer, if necessary.
The permitted range of ambient temperature is -55 °C to +60 °C.