Ex ec IIC T4 Gc
This certificate is issued as verification that a sample(s), representative of production, was assessed and tested and found to comply with the IEC Standard list below and that the manufacturer's quality system, relating to the Ex products covered by this certificate, was assessed and found to comply with the IECEx Quality system requirements. This certificate is granted subject to the conditions as set out in IECEx Scheme Rules, IECEx 02 and Operational Documents as amended.
This Unit verification certificate is issued as verification that the Apparatus identified on page 1, was assessed and tested and found to comply with the IEC Standard list below. This certificate is granted subject to the conditions as set out in IECEx Scheme Rules, IECEx 02 and Operational Documents as amended.
The apparatus and any acceptable variations to it specified in the schedule of this certificate and the identified documents, was found to comply with the following standards:
As this is a Unit Verification Certificate, no QAR is applicable as this certificate is specific to the items listed by serial number or other unique identification.
SMART Transmitter Power Supply Model HiC2025 is for the supply of intrinsically safe transmitters located in an explosive atmosphere and can also be used with an active intrinsically safe current source. It transfers the analog input signal to the non-intrinsically safe side as an isolated current signal.Bi-directional communication is supported for transmitters that use current modulation to transmit data and voltage modulation to receive data.SMART Current Driver Model HiC2031 repeats a 4 - 20 mA input signal from a non-intrinsically safe source to drive intrinsically safe HART I/P converters, valve actuators, and displays located in an explosive atmosphere.The modules mount into a HiC Termination Board.Ambient temperature range -20 ºC to +60 ºC.
- The equipment shall only be used in an area of at least pollution degree 2, as defined in IEC 60664-1.- The equipment shall be installed in an enclosure that provides a minimum ingress protection of IP54 in accordance with IEC 60079-0.- Transient protection shall be provided that is set at a level not exceeding 140% of the peak rated voltage value at the supply terminals to the equipment.
Electrical dataModel HiC2025Supply:19 ... 30 V (via Termination Board),rated current maximum 45 mA,power maximum 1.1 W.Output:4 ... 20 mA or 1 ... 5 V on maximum 300 Ω (source mode) or4 ... 20 mA, 15 … 26 Vdc (sink mode).Model HiC2031Supply:19 ... 30 V (via Termination Board),rated current maximum 30 mA,power maximum 700 mW.Input:4 ... 20 mA (max. 30 mA),maximum 27 V.
Issue 1: Changed type of protection from “nA” to “ec”.