Model 24293A -000, B9G1 CAB. Electrical Ratings 460V, 3-Ph, 60Hz / 230V, 1-Ph, 60Hz / 110V, 1-Ph, 60Hz / 24Vdc
The B9G1 Collector CAB Assembly is component part of a large system and directly connects to end of an electrical generator manufactured by General Electric Power & Water division, USA.
The unit houses various equipment such as the generator collector and turning gear assemblies which are used to start the system and to draw power off during operation. The unit also contains various piping and instrumentation related to the generator monitoring, seal oil supply/drain systems, and hydrogen purging systems. Additionally the unit has gas monitoring, ventilation, lighting, and fire detection/suppression systems installed.
The B9G1 Collector CAB is not a standalone system and is not functional until it is interconnected with a General Electric and properly installed in a Gas Turbine Power Plant.
Junction Boxes in the B9G1 Collector CAB Assembly clearly presents instructions for wiring interconnections and field wiring during final installation of equipment. Instructions for safety, putting into service; use; assembling and dismantling; maintenance, overhaul and repair; Installation; adjustment; is responsibility of General Electric Power & Water division, USA.
NOTE: Although this equipment is covered under a Full Certificate supported by the ExTR and QAR listed, each unit is inspected and verified by the ExCB upon completion. This Certificate covers only the Model Number and Serial Number listed in the “Electrical Apparatus” section on page 1 of this Certificate.