This certificate is issued as verification that a sample(s), representative of production, was assessed and tested and found to comply with the IEC Standard list below and that the manufacturer's quality system, relating to the Ex products covered by this certificate, was assessed and found to comply with the IECEx Quality system requirements. This certificate is granted subject to the conditions as set out in IECEx Scheme Rules, IECEx 02 and Operational Documents as amended.
This Unit verification certificate is issued as verification that the Apparatus identified on page 1, was assessed and tested and found to comply with the IEC Standard list below. This certificate is granted subject to the conditions as set out in IECEx Scheme Rules, IECEx 02 and Operational Documents as amended.
The apparatus and any acceptable variations to it specified in the schedule of this certificate and the identified documents, was found to comply with the following standards:
As this is a Unit Verification Certificate, no QAR is applicable as this certificate is specific to the items listed by serial number or other unique identification.
The Series SM87 General Purpose Alarm Station is designed to provide an electrical signal and an optional indication when an alarm switch is manually operated. It comprises an actuator mechanism with a break glass, a switch, an optional printed circuit board, and various components connected to a terminal block with up to thirteen ways, all housed in a metal enclosure.External connections are made at the terminal block through an entry gland.The Series SM87 comprises the following variants:SM87 BGLI is the standard General Purpose Alarm Station with a glass cover over the actuatorSM87 LBGLI is the same as SM87 BGLI but with a metal flap over the glass coverSM87 PBLI is the same as SM87 BGLI but with a push button actuator, latching mechanism and the glass coverSM87 PBMI is the same SM87 PBLI but without a latching mechanism fitted to actuator.The marking code is: Ex ia IIC T4 Ga (-55°C ≤ Ta ≤ +60°C)Terminal ParametersUi = 29VIi = 147mAPi = 800mWCi = 0Li = 0
This issue permits existing information (for example on Schedule Drawings) to be replaced by the revised certificate holders name. No other changes may be made to the certified design.
File Reference: 16/0725