This certificate is issued as verification that a sample(s), representative of production, was assessed and tested and found to comply with the IEC Standard list below and that the manufacturer's quality system, relating to the Ex products covered by this certificate, was assessed and found to comply with the IECEx Quality system requirements. This certificate is granted subject to the conditions as set out in IECEx Scheme Rules, IECEx 02 and Operational Documents as amended.
This Unit verification certificate is issued as verification that the Apparatus identified on page 1, was assessed and tested and found to comply with the IEC Standard list below. This certificate is granted subject to the conditions as set out in IECEx Scheme Rules, IECEx 02 and Operational Documents as amended.
The electrical apparatus and any acceptable variations to it specified in the schedule of this certificate and the identified documents, was found to comply with the following standards:
As this is a Unit Verification Certificate, no QAR is applicable as this certificate is specific to the items listed by serial number or other unique identification.
An Water-Air Cooled Cage Induction Motor. The motor, of shaft height 500mm, is rated at 4 pole, with a corresponding output of 3900kW and is designed for connection to a 6600V, 3 phase, 60Hz supply.The motor is continuously rated for S1 Duty when connected to a 3 phase supply having form and symmetry not worse than that defined in EN 60034-1 and operated within the defined voltage limits for Zone A and defined frequency limits for Zone A.The mechanical design of the motor is in accordance with the IECEx BAS09.0019X.The main and auxiliary terminal boxes are covered by Ex e certificate IECEx BAS06.0079U.Ambient temperature range -20°C to +40°C.