This certificate is issued as verification that a sample(s), representative of production, was assessed and tested and found to comply with the IEC Standard list below and that the manufacturer's quality system, relating to the Ex products covered by this certificate, was assessed and found to comply with the IECEx Quality system requirements. This certificate is granted subject to the conditions as set out in IECEx Scheme Rules, IECEx 02 and Operational Documents as amended.
This Unit verification certificate is issued as verification that the Apparatus identified on page 1, was assessed and tested and found to comply with the IEC Standard list below. This certificate is granted subject to the conditions as set out in IECEx Scheme Rules, IECEx 02 and Operational Documents as amended.
The electrical apparatus and any acceptable variations to it specified in the schedule of this certificate and the identified documents, was found to comply with the following standards:
As this is a Unit Verification Certificate, no QAR is applicable as this certificate is specific to the items listed by serial number or other unique identification.
This range of cable glands type P*or P*R* is protected by flameproof enclosure, increased safety and dust protection for sizes 1 up to 4 and protected only by increased safety and dust protection for size 0. These cable entries are foreseen, in accordance with the type, for armoured cables or non armoured cables.In accordance to the type, the cable gland can be realised with a simple sealing ring or double sealing ring.The cable glands type P*R*.. are provided with a sealed bushing.These cable glands gets the protection degrees IP66 or IP66/68 according to the standard IEC 60 529 ; the verification of the protection degree IPX8 corresponds to an immersion under 10 meters of water during 6 hours.
The temperature of the enclosure, at the connection point of the cable entry must not exceed the following values :For the type P** or P*R*:
The minimum temperature for use is -40°C for sealing ring in EPDM and -60°C for sealing ring in silicone.
The user shall use cables with thermal stability in accordance with the temperature of the sealing ring.
The clamping of the cables, for the cable glands must be realized oustside of the enclosure, nearby to the enclosure on which the cable glands are installed.
In order to maintained the IPX8 the cable entry shall be fitted on enclosure which satisfies an immersion test under 10 meters of water during 6 hours.