Ex e II T6Ex tD A21 IP66/IP68 (2 m) T85 °C
This certificate is issued as verification that a sample(s), representative of production, was assessed and tested and found to comply with the IEC Standard list below and that the manufacturer's quality system, relating to the Ex products covered by this certificate, was assessed and found to comply with the IECEx Quality system requirements. This certificate is granted subject to the conditions as set out in IECEx Scheme Rules, IECEx 02 and Operational Documents as amended.
This Unit verification certificate is issued as verification that the Apparatus identified on page 1, was assessed and tested and found to comply with the IEC Standard list below. This certificate is granted subject to the conditions as set out in IECEx Scheme Rules, IECEx 02 and Operational Documents as amended.
The apparatus and any acceptable variations to it specified in the schedule of this certificate and the identified documents, was found to comply with the following standards:
As this is a Unit Verification Certificate, no QAR is applicable as this certificate is specific to the items listed by serial number or other unique identification.
The Klik Lok range of junction boxes are manufactured in black, 30% glass reinforced, Polyamide 66 (PA66) with a lid manufactured from the same material or in clear polycarbonate.
The junction boxes have a circular shape, with cable entry locations in the curved side wall. The entry points are available in various configurations. The lid is fitted with a nitrile rubber gasket and is attached and secured to the base by a locking mechanism, a retaining strap and by a cable tie. Inside the enclosure, a terminal rail is fixed to the base with screws.
Certified, rail mounted, Weidmuller terminals or Kwikblok terminals are fitted to the rail between partitions and end stops.
The appropriate details of the Weidmuller and Kwikblok terminals are detailed in Tables 1 and 2 respectively. See Annexe for tables
1. The Klik Lok junction boxes are only to be installed into areas of low mechanical danger.
2. When the clear polycarbonate lids are fitted the equipment is marked: WARNING STATIC HAZARD CLEAN WITH A DAMP CLOTH. Refer to the instruction manual for further advice on how to clean the equipment safely and prevent static charge build up.
Original dated 2006-8-15Issue 1 dated 2008-03-311. The inclusion of an additional manufacturing location2. The addition of additional Weidmüller Terminals